HDPE Water Supply Pipe 315 PE Farmland Irrigation Steel Mesh Skeleton Composite Pipe 100PE Brand New Material
HDPE pipe is a pipe made of high-density polyethylene.
HDPE pipe is a replacement product of traditional steel pipes and PVC drinking water pipes.
|SDR 9||SDR 11||SDR 13.6||SDR 17||SDR 21||SDR 26|
1. It is recommended to take sheltering measures for outdoor laying in the open air and places exposed to sunlight.
2. Buried HDPE water supply pipelines, pipelines with DN≤110 can be installed in a serpentine shape in summer, pipelines with DN≥110 have sufficient soil resistance and can resist thermal stress, so there is no need to reserve a pipe length; in winter, there is no need Reserve the tube length.
3. When installing HDPE pipelines, if the operating space is too small (such as: pipeline wells, ceiling construction, etc.), electrofusion connection methods should be used.
4. When connecting hot-melt sockets, the heating temperature should not be too high or too long, and the temperature should be controlled at 210±10℃, otherwise it will cause too much squeeze out of the fittings and reduce the inner diameter of the water; the pipe fittings are inserted. Or the pipe interface should be clean, otherwise it will cause the socket to break off and leak; at the same time, pay attention to control the angle and direction of the pipe to avoid rework.
5. When connecting hot melt butting, the voltage is required to be between 200~220V. If the voltage is too high, the temperature of the heating plate will be too high and the voltage will be too low. It will cause insufficient butt joint area, insufficient weld strength, and improper crimping; when the heating plate is heated, the pipe interface is not cleaned, or the heating plate has impurities such as oil and sand, which will cause the joint to detach and leak; heating time It must be controlled well. The heating time is short and the pipe heat absorption time is not enough, which will cause the welding edge to be too small, and the heating time will be too long, which will cause the welding edge to be too large, and may form a false weld.
HDPE pipes are mainly used for: municipal engineering water supply system, building indoor water supply system, outdoor buried water supply system and residential area, factory area buried water supply system, old pipeline repair, water treatment engineering pipeline system, gardening, irrigation and other fields of industry Water pipes, etc.
High Mountain Pipe is A company specializing in the production of PE water supply pipes, PE gas pipes and PE flame-retardant, anti-static mining pipes, PE ground source heat pump pipes, PE siphon drainage pipes, PERT floor heating pipes and supporting PE water supply pipes, PE gas pipes, PE flame retardant, anti- High-tech enterprise of series products such as double-resistance pipe fittings for electrostatic mine, PE ground source heat pump pipe fittings, PE sprayed anticorrosive steel flanges, PE ball valves, PERT floor heating pipe fittings, PE siphon drainage pipe fittings, etc.
Q: Can you make special designs and logos on your products?
A: Yes, it is very easy.
Q: What is your warranty policy?
A: The product is guaranteed for two years from the date of shipment (or leaving the seller's factory depending on the terms).
It is also guaranteed that the product can be used for 50 years.
Q: How do you guarantee that the products you provide are qualified?
A: We always believe that integrity and responsibility are the foundation of a company, so any products we provide you are qualified. We will test the goods and provide COA before delivery.
|Contact Person :||Anna qian|
|Tel :||+86 15852662859|